High Pressure, Deep Well Stainless Steel 4 Inch Submersible Water Pump. 2 HP Single Phase 220 - 240 Volt, Liquid Cooled (Oil Filled) Motor.
Pump Condition Point is 11.14GPM & 364Ft. This is a brand new in the box 4 inch pump. The pump has a built in check valve and a 1-1/4 inch threaded discharge. The motor is a 3-wires motor. This is a 2 HP, 15 stage pump.It will deliver 11.14 GPM & 364 ft at its Best Efficiency Point. Please check the pump performance curve below for the full range of pump operation. Almost all components of this pump are made of 316 or 304 stainless steel, except the impellers (made of POM which stands for Polyoxymethylene), the diffusers made of.
PC which stands for Polycarbonate. And both suction and discharge heads which are made of cast bronze. Please check the material of construction table below. Actual test results of this pump are shown below. Maximum flow of this pump is estimated at 22 Gallons/Minute.
Total developed head at the shut-off condition isabout 500 feet, utilizing 15 stages. The best efficiency point, this pump. The motor is single phase, 2 HP, liquid-cooled. It will run on 220 - 240 volt, 60Hz. (pump will run at 3450 rpm) - wiring and installation must be done by a.Professional electrician and a professional installer. The pump is packed in a stout cardboard box. The Cardboard box is 6" x 7" x 51, and weighs in at 38 lbs. The control box is packed in the same box with the pump. Item must be complete, unused and in as new condition. What cable/wire size should I use with this pump? On the full load current and how far is your service panel from your motor as well as the cable material you select copper vs. The following table is an excellent starting point. Beside suggesting the wire size, it also suggests the fuse and breaker sizes!! It was compiled and published (copywrite 1989) by G & G Electric and Plumbing of Washington.
For example, for a 2 hp, 230 volt, single phase, select your motor hp in the 230 volt section. Move horizontally to the distance between the motor and the electric panel. If your distance is equal to or less than 151 feet then the minimum wire size is #12. If the distance is greater than 151 feet but less than 241 feet, you should use a wire size #10.What is the recommended well casing diameter suitable for this pump? Health has a very good web page addressing everything related to well. As well as well casing. Briefly, here is what it has to say about the well casing.
All wells should be cased to a depth of at least 25 feet below ground surface. The casings of wells developed in sand or gravel should extend watertight to or into the aquifer. The minimum casing diameter for every new well should be at least 5 inches nominal inside diameter. Further, the inside well diameter should be at least 1 inch larger than the outer diameter of pumping equipment to be installed.Only those wells used for monitoring may be constructed of casing less than 4 inches in diameter. Thank you for visiting my listings. The item "364 FT@11.14 GPM 4 SUBMERSIBLE SINGLE PHASE 240V 60Hz 2 HP DEEP WELL WATER PUMP" is in sale since Tuesday, November 22, 2016. This item is in the category "Home & Garden\Home Improvement\Plumbing & Fixtures\Pumps". The seller is "ohio*submersible*pumps" and is located in Columbus, Ohio.
This item can be shipped to North, South, or Latin America, all countries in Europe, Australia, Japan, China, South Korea, Taiwan, South africa, Thailand, Hong Kong, Israel, New Zealand, Philippines, Singapore, Saudi arabia, United arab emirates, Qatar, Kuwait, Bahrain, Malaysia.